Citel DS60PV-500 500VDC Grid Tie Surge ArrestorDS60PV are Type 1 heavy duty surge protectors, recommended when a direct lightning strike is possible on the installation. They are available in 500- and 1000-VDC operating voltages. The use of Type 1 surge protector is recommended at both ends of the DC power supply line (solar array side and inverter/converter side). The DS60PV is made with a monobloc enclosure and mounts on DIN rail.
Citel PV surge protectors are DIN mount and are ideal for placement inside combiner boxes.
DC Power Surge Protection Overview
Solar Photovoltaic (PV) Systems are very demanding and cost intensive projects. They often require the Solar PV System to be operational for several decades before it can yield the desired return on investment.
Many manufacturers will guarantee a system life of greater than 20 years while the inverter is generally guaranteed for only 5-10 years. All costs and return on investments are calculated based on these time periods. However, many PV systems are not reaching maturity due to the exposed nature of these applications and its interconnection back to the AC utility grid. The solar PV arrays, with its metallic frame and mounted in the open or on roof tops, act as a very good lightning rod. For this reason, it is prudent to invest in surge protection to eliminate these potential threats and thus maximize the systems life expectancy. The cost for a comprehensive surge protection system is less than 1% of the total system expenditure.
To analyze the full threat level of the installation, we must make a risk assessment.
Operational Downtime Risk –
|Areas with severe lightning and unstable utility power are more vulnerable.
Power Interconnection Risk –
|The greater the surface area of the solar PV array, the more exposure to direct and/or induced lightning surges.
Application Surface Area Risk –
|The AC utility grid is a likely source of switching transients and/or induced lightning surges.
Geographic Risk –
|Consequences of system downtime are not only limited to equipment replacement. Additional losses can result from lost orders, idle workers, overtime, customer/management dissatisfaction, expedited freight charges and expedited shipping costs.
1) Earthing System
Surge Protectors shunt transients to the earth grounding system. A low impedance ground path, at the same potential, is critical for the surge protectors to function properly. All power systems, communication lines, grounded and ungrounded metallic objects need to be equipotentially bonded for the protection scheme to work efficiently.
2) Underground Connection from External PV Array to Electrical Control Equipment
If possible, the connection between the external Solar PV Array and the internal power control equipment should be underground or electrically shielded to limit the risk of direct lightning strikes and/or coupling.
3) Coordinated Protection Scheme
All available power and communication networks should be addressed with surge protection to eliminate PV system vulnerabilities. This would include the primary AC utility power supply, Inverter AC output, Inverter DC input, PV string combiner and other related data/signal lines such as RS-485, 4-20mA current loop, PT-100, RTD, and telephone modems.